[Beowulf] A/C to water cooling, considering the transition
josip at lanl.gov
Thu Apr 14 16:21:48 EDT 2005
David Mathog wrote:
> Or is chilled water too cold for direct use in cooling
> computer equipment? (For nstance, causing condensation
I'm not sure that you'd be using pure chilled water to cool your CPUs
directly. Apple's liquid cooled Mac uses some kind of alcohol, I think.
Since air cooling dominates today, there are also transitional
technologies to consider. A mixed air/water cooling scenario involves a
water-cooled rear door to cool the hot air coming out of a rack; this
doesn't cause condensation if that the liquid is not too cold.
See http://www.designnews.com/article/CA500772.html for an example:
Altix systems can dissipate ~8KW per rack, so they use a water cooled
rear door, which works with chilled liquid of just under 60 deg. F.
Just in case any condensation happens anyway, they added a drain feature
to the rack.
Given the rapid increases in packaging density (e.g. blade servers with
power densities much higher than SGI's Altix), I'm pretty sure that
large computer installations will want liquid cooling. Making this
transition is a challenge today, but within a few years, more plumbing
will be needed in high end computer rooms.
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf