[Beowulf] rear door heat exchangers
Michael Di Domenico
mdidomenico4 at gmail.com
Wed Feb 1 08:23:06 EST 2012
On Tue, Jan 31, 2012 at 6:47 PM, Lux, Jim (337C)
<james.p.lux at jpl.nasa.gov> wrote:
> Maybe there's an issue with the weight and or flexible tubing on a swinging door?
> The Hoffman products in Andrew's email, I think, aren't the kind that hang on a door, more hang on the side of a large box/cabinet (Type 4,12, 3R enclosure) or wall.
> They're also air/air heat exchanges or airconditioners (and vortex coolers.. but you don't want one of those unless you have a LOT of compressed air available)
> shows "in-row liquid cooling" but I think that's sort of in parallel
> They do mention, lower down on the page, "Rear Door Liquid Cooling"
> But I notice that the Liebert XDF-5 which is basically a rack and chiller deck in one, only pulls out 14kW.
> From DoE:
> They refer the ones installed at LLBL as RDHx units, but carefully avoid telling you the brand or any decent data. They do say they cost $6k/door, and suck up 10-11kW/rack with 9 gal/min flow of 72F water.
> Googling RDHx turns up "CoolCentric.com"
> 33kW is as good as they can do.
> I also note that they have no fans in them.
Yes, these are the doors we have now. I was trying to remain vendor
agnostic on the list. We have them running well passively up to 25kw
Beowulf mailing list, Beowulf at beowulf.org sponsored by Penguin Computing
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
This message has been scanned for viruses and
dangerous content by MailScanner, and is
believed to be clean.
More information about the Beowulf