[Beowulf] precise synchronization of system clocks
Lux, James P
james.p.lux at jpl.nasa.gov
Thu Oct 2 09:37:58 EDT 2008
> I understand inductive surge when powering up, I understand in detail
> browning out a primary power transformer, but I think those are
> different issues and irrelevant here.
Inductive surge -> magnetizing current in large iron core inductors (depends
on where you are in line frequency cycle at "switch on")
Sag from overload -> impedance (both R and L) in transformer and wires from
transformer to load. 2% voltage drop is the NEC guideline for "in premises
wires".. From panel to load. The voltage at the utility entrance could
probably be +/- 5% at any given time.
> So far, using my trusty Kill-a-Watt on real world nodes, I haven't seen
> more than a 30% differential draw loaded to unloaded. Large parts of
> the CPU require power at all times to function. Memory, for example,
> both on and offboard. Nearly everything inside a computer has a
> nontrivial idle draw, plus (sure) peak draw when it or one of its
> subsystems are in use.
Very much true. DRAM needs refresh, for instance.
> Exceptions are modern laptops -- with variable speed clocks, they draw
> much less idling than they do at speed, in part because power (idle or
> otherwise) IS very nearly proportional to CPU clock in at least parts of
> the system. And I don't really know how the latest designs do in this
> Multicores, of course, may function like hybrid cars, and somehow run
> more nearly idle when they are idle. But I'd have to hear from someone
> who slapped a KaW on an actual system and clocked it from idle (solidly
> post-boot, running the OS, at idle "equilibrium") to loaded (running
> flat out on e.g. a benchmark suite that loads all cores and/or the
> memory etc.). Has anyone actually done this and observed (say) a 2 or 3
> to 1 increase in power draw loaded to idle? 50W idle to 200W loaded in
> 1 second? 150W idle to 200W loaded is more like what I've seen...
Don't forget that the power supply efficiency drops dramatically when DC
load drops, too. They don't spend a penny more on sophisticated design than
required to get that "energy star" rating, and that has more to do with
having a good "low power hibernate" mode than good efficiency at 25% load.
>> In normal practice I doubt that this is an issue but synchronization in the
>> extreme is interesting in its details and side effects.
> I completely agree with this, both parts. Although if one IS bumping
> from 50->200W "instantly" on not even an entire cluster but just all the
> nodes on a single circuit, that's popping over a KW on a 20A line --
> ballpark where one MIGHT see something inductive (although as I said,
> probably nothing that the power supply capacitor(s) cannot buffer,
> although I'm too tired to compute the number of joules (watt-seconds)
> one can probably deliver and what RC probably is, etc). Popping
> multiple (as in 10+) KW in less than a 60 Hz cycle would very likely be
> hard on the primary, no doubt about it.
If one considers that a single wire is about 1 uH/meter (typical electrical
wiring will be much less, because it's a pair, with currents flowing
opposite directions), the series L might be a few tens of uH. At, say, 20
A, there's just not much energy stored there.
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf