[Beowulf] Thermals question
hahn at mcmaster.ca
Wed Apr 23 14:22:47 EDT 2008
> This link has a lot of good information and might answer your question:
as long as you're alert to the fact that it's an APC marketing document.
It is unlikely that a traditional data center, with computer room air
conditioning (CRAC) units supplying airflow through a raised-floor plenum,
will be able to deliver a cooling capacity of more than 3 kW to any rack,
regardless of quantity and capacity of CRAC units and floor depth.
by "traditional", perhaps the author means "designed for < 3kW/rack",
but if so, the sentence implodes...
a traditional data center with a simple ~14" raised-floor and free-air return
can indeed cool >10 KW racks just fine. the first few suggestions (maintain
your chillers, install blanking panels, tidy up your cables) are fine, and I
hope fairly obvious. items 5-8 are all somewhat arguable. interestingly, I
was worried about figure 10 (suction in tiles too near the chiller), but am
surprised that even as close as 6 feet from a high-velocity outflow, tile
flow is adequate and upward. items 9,10 are just APC sales pitches.
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf