[Beowulf] Re: Emergency Power Off
James.P.Lux at jpl.nasa.gov
Fri Mar 23 12:41:46 EDT 2007
>I've been looking for an off the shelf EPO solution, but so far the only
>things I've found are for huge data centers. Anybody know of a product
>in my size range, to control roughly 10 EPO shut offs? There's a point
>where adding more switch blocks becomes a bit awkward.
Relays are your friend.
EPO switch has Normally Closed contacts (i.e. they open when you hit
Power flows through contacts to small relay with NO and NC contacts
(you can use DC or AC supplies)
relay contacts go to UPSes
Multiple relays can be paralleled.
It's "fail safe" because if the AC power to the relay system fails,
the relays drop out, and turn off the UPSes.
>mathog at caltech.edu
>Manager, Sequence Analysis Facility, Biology Division, Caltech
James Lux, P.E.
Spacecraft Radio Frequency Subsystems Group
Flight Communications Systems Section
Jet Propulsion Laboratory, Mail Stop 161-213
4800 Oak Grove Drive
Pasadena CA 91109
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf