Robert G. Brown
rgb at phy.duke.edu
Fri Nov 1 15:43:11 EST 2002
On Fri, 1 Nov 2002, David Mathog wrote:
> > I'm not sure what this means. 15A "plug"? Either this is horribly
> > dangerous and a code violation or irrelevant -- if you use a 20A
> > breaker, everything in your circuit downstream had better be rated for
> > 20A or be fused for lower current operation so you can't start a fire
> > and not blow the (or a) breaker first.
> You're absolutely right.
> The room is wired correctly - I misidentifed the plug types.
> The wire molding is darkish gray and runs along the wall beneath
> the table surfaces - so there isn't a lot of light or contrast.
> Inspected up close with a flashlight the receptacles are clearly
> 5-20R. Oddly, even knowing this, looking at them with normal room
> light from 8 feet out they still look like 5-15Rs to me.
Sorry to rant a bit about it, but after our experiences with wiring here
I don't take much for granted anymore. If they WERE 15A receptacles,
you'd be needing to rant a bit too...:-)
Robert G. Brown http://www.phy.duke.edu/~rgb/
Duke University Dept. of Physics, Box 90305
Durham, N.C. 27708-0305
Phone: 1-919-660-2567 Fax: 919-660-2525 email:rgb at phy.duke.edu
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf