mathog at mendel.bio.caltech.edu
Fri Nov 1 11:59:37 EST 2002
> I'm not sure what this means. 15A "plug"? Either this is horribly
> dangerous and a code violation or irrelevant -- if you use a 20A
> breaker, everything in your circuit downstream had better be rated for
> 20A or be fused for lower current operation so you can't start a fire
> and not blow the (or a) breaker first.
You're absolutely right.
The room is wired correctly - I misidentifed the plug types.
The wire molding is darkish gray and runs along the wall beneath
the table surfaces - so there isn't a lot of light or contrast.
Inspected up close with a flashlight the receptacles are clearly
5-20R. Oddly, even knowing this, looking at them with normal room
light from 8 feet out they still look like 5-15Rs to me.
Guess I need new eyes too.
mathog at caltech.edu
Manager, Sequence Analysis Facility, Biology Division, Caltech
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf