Dual AMD systems in rackmount cases
hahn at physics.mcmaster.ca
Mon Jun 24 14:19:09 EDT 2002
> > Does anybody have any experience with Dual AMD systems (MP2000) in 2 RU
> > rackmount cases? Is heat generation a problem? I am planning on
there seem to be quite a lot of vendors who seem confident enough
to sell dual AMD 1U's. I don't see a lot of 2U's; my impression
is that the engineering for such boxes is strictly based on flow,
and that the increased dead-air capacity of 2U doesn't buy you much.
> > building a system with Tyan 2466 motherboards and 400 W power
> > supplies. Should I use 3RU cases?
if you can afford the lower density, go for it! is 3U high enough
to handle normal upright PCI cards? risers for low-profile cases
appear to be a source of some difficulty...
racksaver, for instance, seems comfortable letting you configure
a dual athMP/2100 right now. apparently the thoroughbred version
will save just a handful of wats.
> As important as these two components is being able to provide ambient
> air at around 65F (or cooler, of course:-) on the air intake side of the
> cases and to get rid of the 75F air coming out of the air outflow side
75 seems a little conservative on exhaust temp, though I suppose it
depends hugely on the volume of air you're talking about. my machineroom
(currently 30 KW of alphas, but soon to have 5-10KW new ia32's)
registers around 60-65 in the cold ducts, and around 85 in return.
and, importantly I think, there's a pretty clear and strong airflow
> Dual AMD's will just plain crash when they get hot, and they get hot
> very, very easily as they draw about 150 W sustained under load. In our
AMD's pushing vendors to implement thermal management, but I'm not
clear on how well it all works.
> new server room, our 2U cases were not originally getting enough, cold
> enough, air and the temperature at the case rears was up in the 80's.
it depends on how "dilluted" that 80F is - by itself, 80F is still
quite cool: suppose you have a CPU dissipating 70W, and your HS/fan
will need 20-25C of thermal gradient. since you don't want your CPU
at its rated max (usually 90C), but say 60C, you need fan ambient
to be 95F or less.
> KW/meter^3 seems unwise -- any sort of bobble in your cooling system
> will rapidly cause your stack to reach furnace temperatures, and even
ah, well, I think you have to start with assuming *something* stays up.
I'm assuming that I can shut down my space heaters if (when) our chilled
water goes out (again)...
regards, mark hahn.
Beowulf mailing list, Beowulf at beowulf.org
To change your subscription (digest mode or unsubscribe) visit http://www.beowulf.org/mailman/listinfo/beowulf
More information about the Beowulf